Lithium-Ion (Li-Ion or LIB)
Lithium batteries have mostly been used where size and weight is important such as for small electronic devices, portable equipment, electric vehicles and other mobile applications. More recently, the high cycle life of lithium has made it applicable with self consumption grid-tied applications and the high current capability has made lithium a good choice for larger UPS systems. Due to the high cost of lithium batteries, they have not played a major role for stationary solar off-grid applications. However, this seems to be changing to some extent with the lowering costs and more lithium batteries becoming available.
There are several advantages with Lithium batteries including the following.
Possible disadvantages with lithium are as follows.
Requirements for using Morningstar Controllers typically include the following.
Morningstar controllers do not include a BMS for lithium batteries. The use of Morningstar controllers with lithium batteries is limited to the same type of voltage regulation limits that are provided for lead acid batteries. Therefore, if there are imbalances between cells Morningstar controllers will not protect lithium batteries from cell over-voltages or under-voltages. Many lithium batteries include a BMS that can implement an internal battery disconnect. It is important that the battery will not implement an internal disconnect during charging. The best solution for prevent this is to use a BMS that can either disconnect the array input to the controller or disable charging with the controller by forcing a remote temperature sensor (RTS) disconnect. Another solution is to use conservative settings and monitoring of the battery cells to ensure that this will not occur. Damage to the controller due to a battery disconnect during charging is typically not covered under warranty. Incidental damage to loads due to voltage surges upon a battery disconnect is also not covered under warranty.
Morningstar recommends using caution when charging Lithium batteries. Every Lithium battery is different. Even if it is made up of the same type of battery cells there can be differences between the BMS solutions which can make a significant difference in behavior and performance of the battery. In addition to the Morningstar disclaimer regarding information on this website below, it is the installer and end user’s responsibility to eliminate the potential of any problems when designing, installing and using lithium batteries with any Morningstar product.
Morningstar provides data logging for Morningstar products and some lithium batteries include data logging of the battery cells which is recommended as a best practice to detect potential problems with the system if external charge and load disabling is not possible with the BMS system.
ProStar MPPT and ProStar (Gen 3) Low Temperature Foldback
The ProStar MPPT and 3rd generation ProStar include Low Temperature Foldback which can be used to protect lithium batteries from being charged in cold conditions. The custom settings temperature thresholds which defines the bounds of charge current reduction due to low battery temperature can be programming in MSView or with the Advanced Custom settings options with the display interface which is available with the built-in meter models of the ProStar MPPT (PS-MPPT-25M and PS-MPPT-40M).
The High Limit defines the lowest temperature at which the controller will deliver 100% of the controller’s rated output charging current. The Low Limit defines the temperature at which the controller will stop providing battery charging current. The charge current is tapered linearly from the High Limit to the Low Limit.
Example with NEC Energy Solutions ALM12V35 battery: High Limit 10C, Low Limit -20C, PSMPPT-25 (25A controller); at > 10C battery temperature controller will deliver 25A max charging current (if available); at -5C battery temperature it will deliver 12.5A max (if available); below -20C will deliver 0A.
The graph above displays the maximum charge current in blue for the NEC ALM-35 Lithium battery with a custom programmed Low Temperature Foldback for the PS-MPPT-25 controller. This will allow the controller to continue to operate when the battery is exposed to low temperatures as measured with Morningstar’s remote temperature sensor (RTS) and allows it to recover the battery operation during low temperature conditions. It should be noted that the RTS might not always be measuring the same temperature as the lowest cell temperature of the battery. This is where monitoring the lithium battery cell temperature can be considered in order to verify that there will not be a problem with the settings.
Disclaimer: Morningstar makes no representation, warranty or assumption of liability regarding the information presented on this web site regarding the various charging requirements for any type of battery or model. The material being presented is based on information that has been provided by other parties (such as battery specs and operational parameters) and uses assumptions which may or may not prove to be valid or up to date.